cable suitable for direct burial
max. permitted temperature at conductor 90 °C
min. installation temperature -20 °C
installation in free air without UV-protection (cable UV-resistant)
cable for use in water
cable with VDE-certification
- Item list
- Technical data
- Technical documents
|Conductor material||copper, bare|
|Conductor class||class 2 = stranded|
|Sheathing material||polyethylene DMP2|
|Colour outer sheath||black|
|For outdoor use||yes|
|Maximum permitted conductor temperature, °C||90 °C|
|Permitted outer cable temperature, fixed, °C||70 °C|
|Permitted outer cable temperature, in motion/during installation, °C||-20 - +70 °C|
|Bending radius, fixed installation||15 x DA|
|Number of cores||1|
|Wall thickness of sheath||2.5 mm|
|Colour of outer sheath||black|
For installation in the ground, in water, outdoors, indoors and in cable ducts for power stations, industrial applications and distribution networks. It should be noted during installation in cable ducts and interior spaces that the PE-sheath is zero-halogen, yet not flame-retardant as defined under DIN VDE 0482-332-1. This cable is also suitable for unfavourable operating conditions, specifically where there is a need to avoid water penetration lengthwise following mechanical damage.
All images shown here are for illustrations and product reference purposes only.
Freight cost extra. Prices plus metall regarding the daily market price.